Three phase applications available as well
Motor: 1/6 HP 115 volt / 1 phase
Wheel Diameter- 10″ Diameter
Loren Cook Model #: 101W17D
REPLACEMENT MOTOR SINGLE PHASE 115 VOLT: Please call or email for pricing
REPLACEMENT MOTOR THREE PHASE: Please call or email for pricing
REPLACEMENT BEARINGS: Please call or email for pricing
REPLACEMENT SHAFT: Please call or email for pricing
REPLACEMENT BLADE: Please call or email for pricing
REPLACEMENT TOPCAP/LID: Please call or email for pricing
ACWD Aluminum Centrifugal Wall Mounted Direct
LOREN COOK COMPANY certifies that the ACWD, ACWD-EC, ACWD-HP, ACWDEC-HP, ACWD-XP, and ACWDEC-XP shown herein are licensed to bear the AMCA Seal. The ratings shown are based on tests and procedures performed in accordance with AMCA Publication 211 and AMCA Publication 311 and comply with the requirements of the AMCA Certified Ratings Program.Type ACWD, ACWD-EC, ACWD-HP, ACWDEC-HP, ACWD-XP, and ACWDEC-XP are furnished standard with UL 705 and cUL 705 listings (Power Ventilator/ZACT).
All sizes are available with express service.
Designed specifically for wall mounting, to discharge contaminated air perpendicular to a wall.
Description – Fan shall be a spun aluminum, wall mounted, direct driven, horizontal centrifugal exhaust ventilator.
Certifications – Fan shall be manufactured at an ISO 9001 certified facility. Fan shall be listed by Underwriters Laboratories (UL 705) and UL listed for Canada (cUL 705). Fan shall bear the AMCA Certified Ratings Seal for Sound and Air Performance.
Construction – Fan shall be of bolted and welded construction utilizing corrosion resistant fasteners. The spun aluminum structural components shall be constructed of minimum 16 gauge marine alloy aluminum, bolted to a rigid aluminum support structure. The spun aluminum wall flange shall have pre-punched keyslot holes and a mounting template with wall opening location for ease of installation. The windband shall have a rolled bead for added strength. An integral conduit chase shall be provided into the motor compartment to facilitate wiring connections. The motor shall be enclosed in a weather-tight compartment, separated from the exhaust airstream. Unit shall bear an engraved aluminum nameplate. Nameplate shall indicate design CFM and static pressure. Unit shall be shipped in ISTA Certified Transit Tested Packaging.
Wheel – Wheel shall be centrifugal backward inclined, constructed of 100 percent aluminum, including a precision machined cast aluminum hub. Wheel inlet shall overlap an aerodynamic aluminum inlet cone to provide maximum performance and efficiency. Wheel shall be balanced in accordance with AMCA Standard 204-05, Balance Quality and Vibration Levels for Fans.
Motor: Motor shall be NEMA design B with a minimum of class B insulation rated for continuous duty and furnished at the specified voltage, phase and enclosure.
Motor (EC): Motor shall be an electronically commutated motor rated for continuous duty and furnished either with internally mounted potentiometer speed controllor with leads for connection to 0-10 VDC external controller.
Product – Fans shall be models ACWD, ACWD-EC, ACWDEC-HP, ACWDEC-XP, ACWD-HP or ACWD-XP as manufactured by LOREN COOK COMPANY of Springfield, Missouri.
OPTIONS – These additional accessories will result in cost variation! Contact us for additional cost on these accessories! These options are not included on the product above!
- Gravity Damper. (UL705 Only)
- Motorized Damper. (UL705 Only)
- Wall Mount Sleeve.
- Roof Curb. (Vented and Non-Vented)
- Grease Collection Box. (Size 12 & larger)
- Bird Screen. (UL705 Only)
- Base Hinging Kit or Hinged Sub Base. (for NFPA96 compliance)
- Combination package that includes a supply fan mounted on the same roof curb.
|Fan Size||A||B||C||D Wall Opening||T Dia||Approximate