Vane Axial Fan
Description: Fan shall be a fixed pitch, belt drive vane axial fan.
Certifications: Fan shall be manufactured at an ISO 9001 certified facility. Fan shall be listed by Underwriters Laboratories (UL 705) and UL listed for Canada (cUL 705). Fan shall bear the AMCA Certified Ratings Seal for Sound and Air Performance.
Construction: Fan shall be of bolted and welded construction utilizing corrosion resistant fasteners. Housing shall be minimum 12 gauge steel with continuously welded seam. Housing shall incorporate continuously welded, inlet and outlet flanges of minimum 1-1/4” x 1-1/4 x 1/4” and be pre-punched for mounting. Housing shall include nine continuously welded steel discharge vanes and aerodynamically designed belt tunnel. Copper lube lines shall be extended from the bearings to the outside of the housing. Pivoting motor plate shall utilize threaded L-bolt design for positive belt tensioning. Unit shall bear an engraved aluminum nameplate.
Coating: All steel fan components shall be Lorenized® with an electrostatically applied, baked polyester powder coating. Each component shall be subject to a five stage environmentally friendly wash system, followed by a minimum 2 mil thick baked powder finish. Paint must exceed 1,000 hour salt spray under ASTM B117 test method.
Showing all 7 results